Many common software questions are answered in the categories below. If you can’t find a response for yours, try checking our User Forum, or, contact HelpDesk for direct assistance
|MarketManager » Loads and Sizing|
Each zone is evaluated at *its* design hour (changeable in Zone Detail), and all zonal loads are added up to give the system load.
If you leave all zone design hours @ 4 p.m. (the default) then you effectively have coil loads at 4 p.m. which may or may not be the peak of anything (but usually is).
You can "play" with each zone design hour and adjust it to *its* individual peak, or change them all together and see when their sum peaks. You can find when the individual zones peak by looking at the data field "zone loads" in the data group "zone" in diagnostics. Each item number represents a different zone (where zone number = item number).
I can’t find the answer to your question ? Try checking our User Forums.
Otherwise feel free to contact our Tech Support staff at (805) 329-6565, or via email at email@example.com.